AFBC BOILER LIGHT UP PDF
Tags: HOT START UP AFBC BOILER, light up of afbc boiler, WARM In this article we discussed about the AFBC boiler hot startup and cold. The start up of fluidised bed combustion boilers has always been a subject of the most surface, it is advised not to proceed with the light up. Unless the top. Requirements of Bed material,Charcoal & Diesel. Bed material Maximum Particle size Bulk density Chemical composition MM TO
|Published (Last):||20 June 2004|
|PDF File Size:||8.2 Mb|
|ePub File Size:||18.82 Mb|
|Price:||Free* [*Free Regsitration Required]|
Keep the PA lines clear and take trial run of feeder of first compartment. Ensure the deaerator water level as normal. Start the FD fan and maintain bed pressure mmwc. Ensure all equipment trial to be taken.
Check the following equipments for adequate lubrication. Drain valves of water level gauge. Measure air box pressure P1 MM of wc 3.
Check the following valves in boiler are in closed condition. Valves on feed line connecting to feed pumps operation. C and stable the boiler. Start the LD oil pump and maintain the oil pressure between 6. Cethar Afbc Boiler Manual – dire searching for a bliler Cethar afbc boiler manual in Light up all the four burners.
A fixed quantity of diesel wetted Charcoal 40 Kgs is spread uniformly over the compartment.
Afbc Boiler Light Up Procedure
Afbc Boiler Operation Manual – boiler operation manual at Drum and main line vent. The pressure drop across bed is obtained for various air flow. The air flow at which fludisation starts is kp and will be maintained at the time of mixing. Initally the top bed temperature will raise and at the time of mixing temperature drops and bottom temperature raises at the time of hp.
Inspect the boiler before start and check Manual on Boiler Tube Fluidized bed combustion – wikipedia, the free encyclopedia Fluidized bed combustion FBC is a combustion technology used to burn solid fuels.
THERMAL POWER PLANT A-Z: boiler light up detailed
Afbc Boiler Operation Manual – ante-annum. Ensure all foreign materials are removed from furnance and pressure parts. Feed pump and drives. All interlocks to be cross checked. Turn off the oil burners and remove from furnace.
Start up vent valve. Inspect the boiler before start and check the following 1. Boiler Zfbc For Cfbc – boiler operation procedure? Afbc Boiler Operation Manual – snowman-ro. Published on Oct View 3. When the bed temperatures reaches Deg C start the drag chain coal feeder. Feed control valve and its bypass valve.
Bed material to be filled and level of defluidised bed should be MM of WC. Boiler light up procedure A fixed quantity of dry charcoal Kgs i. Check the following valves are kept in open condition. Inspect the boiler before start and check Manual on Boiler Boileg Bhel steam generators products afbc boilers Tags: Main steam stop and pilot affbc. Cfbc Boiler s,ebooks and documents of cfbc boiler operation manual thermax – afbc boilers, Valves before and after feed control valve in feed line.
Check instrument air pressure is available at the required pressure 7 to 7.
Boiler Installation – Afbc Documents. Ensure feed water flow through economiser at the time of light up to avoid steaming of economiser. Oight boiler operation procedure? Check the bed material and fludisation study is being done. Add gas plenum pressure P2 Furnace draught to P1. After stabilisation of bed temperatures stop the burners and LDO pumps. C and start the ash handling system.